OCM1 Output Control Module
|Supply voltage||10,5 to 28,5 V|
OCM current consumption:
from ACL, no more than
from power supply source (without the load
connected to outputs), no more than
Relay outputs data:
current commuted by each relay output, no more
current commuted by the whole module (net current
for all outputs at the same time), no more than
Circuit failure test current:
in switched off output condition, no more than
in switched on output condition, no more than
10 mÀ to 210mÀ
|Module overall dimensions, no more than||125õ78õ37 mm|
|Weight, no more than||150 g|
|Operating temperature range||-25° to +55°Ñ|
|Average service life, at least||10 years|
Addressable relay modules are programmable devices.
It is configured by the user with the “FireSec “Administrator” software.
Depending on the output quantity (number of relays), relay module is designed in two versions:
- OCM1 – one output OUTPUT1;
The following equipment and devices can be connected to the addressable relay module:
- illuminated information panels (OPOP 1-8 or similar);
- sound alarms (OPOP 2-35 or similar);
- light and sound alarms (OPOP 124-7 or similar).
OCM module controls the circuit from each relay to actuators for interruption and short circuit in switched-on and switched-off relay condition.
Addressable relay module receives commands to control built-in relays via two-wire unipolar addressable communication line.
Relay module has LED communication indicator with control and indicating panel and the activated relay state indicator.
OCM relay module may be installed in DIN rail using special securing bar (not in the scope of supply; may be provided by separate order).
Relay module is equipped with load connection devices (LCD) the number of which corresponds to the number of outputs to control the line for interruption and short circuit. LCD is a circuit board with installed LEDs, input terminal for relay connection to the line and output terminal for connection to load (actuator).
For interruption and short circuit control of the line, LCD should be connected directly to the load of relay output (to the actuator) according to the Output4 connection diagram shown in the picture. If the integrity of the load circuit needs to be controlled, then connection is provided according to the Output3 connection scheme on the diagram. Instead of LCD, diodes can be used for circuit integrity control. Their connection is shown on connection diagram to Output2. Several devices, i.e. OPOP 1-8 or OPOP 1-8M indication panels may also be connected to the same output. In this case, the indication panels shall be connected to the line in parallel, and one control current diode shall be mounted at the end of the line. Installation diagram is shown on a scheme in case of connection to Output1.
To control “Interruption” state in ON output condition it is necessary to ensure current flow through the load of at least 10 mA. If the LCD's current consumption is less than 10 mA, resistor is connected in parallel to increase the current consumption. However, the majority of devices connected to the outputs of OCM module have a current consumption of more than 10 mA (panel, sirens etc.), in this case the installation of such resistor is not required.
Within the system each relay of the addressable relay module OCM is a stand-alone logical device, i.e. each relay is defined as a stand-alone fully-featured device and takes one address in the system.