|Power supply||12 V or from USB PC|
Number of attachment interfaces:
- “Rubezh” fire alarm control and indicating panels - RS-485, galvanically isolated
- NV 2050 transmitter - COM port according to diagram- USB - for configuring
|RS-485 interface cable length, no more than||1000 m|
USB interface cable length, up to
|Overall dimensions of the module, no more than||84õ125õ37 mm|
|Weight, no more than||200 g|
|Operating temperature range||from 0 to +40°Ñ|
|Average service life||10 years|
MS-4 adapter module is intended for integration of the “Rubezh” addressable system with announcement system for message delivery via the Navigard GSM channels.
MS-4 adapter module collects events from the “Rubezh” addressable control and indicating panels and deliver them to the NV2050 transmitter.
The “Rubezh” control and indicating panel output is connected to MS-4 adapter module input via the RS-485 interface. MS-4 adapter module converts the data received from the “Rubezh” fire alarm control and indicating panels and transmits them to NV2050 transmitter, which, in turn, transmits the signals to NV DG 2010 or NVC DG 3220 receiver of the monitoring station.
Adapter module is powered from power supply of +12 V or USB-terminal of the computer. The time of the adapter module technical availability for operation after power-up is no more than 1 s..
On the front of the device there are LEDs intended to display the current state of the adapter module.
LED indicator "MODE":
- standby indication at a rate of 1 Hz.
LED indicator RS-485 "1":
- when there is no exchange with control and indicating device - off;
- when there is exchange with the control and indicating device, the LED is blinking at a rate of 10 Hz;
- connect MS-4 adapter module to FACIE of the “Rubezh” addressable system via RS-485 interface;
- connect MS-4 adapter module to NV2050 transmitter via COM port.
MS-4 adapter module should be preconfigured before the installation. For configuring, it is necessary to connect MS-4 adapter module to a computer via USB-interface and install SW FireSec 3 on the computer. Start FireSec 3 Administrator, open Project Designer. Add MS-4 adapter module to the list of devices, set its address within the range of 1 to 100. Before saving configuration make sure that all control and indicating panels are listed, otherwise scanning of the device not included in the configuration will not be done. Select MS-4 adapter module in the devices list, open “Device” menu, go to “USB” sub-menu, and select the “Save configuration on device” item. otherwise scanning of the device not included in the configuration will not be done. Select MS-4 adapter module in the list of devices, open menu "Device", go to sub-menu "USB", and select the item "Save configuration on device".