|Power supply||12 V or from USB PC|
Number of attachment interfaces:
FACIE RUBEZH brand - RS-485, electrically isolated;
RS-202TD transmitter – RS-485, non electrically isolated;
USB – for configuring
|RS-485 interface cable length, no more than||1000 m|
|Length of USB interface cable, up to||2 m|
|Overall dimensions of the module, no more than||84х125х37 mm|
|Weight, no more than||200 g|
|Operating temperature range||from 0 to +40°С|
|Average service life||10 years|
In particular, MS-3 adapter module is intended for Rubezh addressable system integration with Lonta-202 system.
MS-3 adapter module collects events from the Rubezh addressable control and indicating panels and deliver them to the RS-202TD-RR transmitter.
Rubezh control and indicating panel’s output is connected to MS-3 adapter module input via RS-485 interface. MS-3 adapter module converts data received from FDCP RUBEZH and transmits them over RS-485 protocol to communicator transmitter RS-202TD-RR for further transmission to monitoring station equipment.
Adapter module MS-3 is powered from power supply +12 V or USB-terminal of the computer. The time of AM technical availability for operation after power-up is no more than 1 s. On the front side of the device there are LEDs intended to display the current state of the adapter module.
- standby indication at a rate of 1 Hz.
LED indicator RS-485 "1":
- when there is no exchange with fire alarm control and indicating panels, the LEDs are off;
- when there is exchange with FACIE, the LED is blinking at a rate of 10 Hz;
LED indicator RS-485 "2":
- when there is data exchange with transmitter, LED is steady on;
- when there is no data exchange with transmitter, LED is off.
For connection of FACIE (fire alarm control and indicating equipment) included in Rubezh addressable system to Lonta-202 system, the following steps shall be taken:
- teach RS-202TD-RR communicator transmitter in the RS-202PN centralized surveillance office (as per Operation Manuals);
- connect MS-3adapter module to FACIE of the RUBEZH addressable system over RS-485 interface.
- connect MS-3 adapter module to RS-202TD-RR communicator transmitter over RS-485 interface.